Things You'll Need
Vacuum with narrow attachment
Burnham is a brand of heating products manufactured by U.S. Boiler Company. The company is based in Lancaster, Pennsylvania, and is a major provider in the residential heating market. Hydronics is the use of water as the medium for heat transfer, as found in boilers. The burner is the central heating mechanism of a boiler and runs on a gas power source. Regular inspection and care of a Burnham gas burner can help optimize its continued performance.
Clean the burner if the boiler has trouble starting or sustaining a flame. Remove the front panel jacket. Disconnect the pilot tubing from the gas valve. Disconnect the sensor cable and ground wire from the ignition module. Disconnect the Flame Rollout Switch wires. Remove the burner access panel. Grasp the burner by the elongated "throat" and lift slightly to clear the orifice. Withdraw the burner from the combustion chamber. Use a soft brush to clean the top of the burner. Use a narrow attachment to vacuum the burner. Vacuum the tip of the Pilot Burner. Clean the firebox by vacuuming it. Reinstall the burner and all components in reverse order.
Video of the Day
Ensure that no objects are obstructing the airflow and ventilation surrounding the boiler. Poor ventilation can hinder the necessary oxygen from reaching the flame. An impeded airflow might snuff the pilot light.
Inspect the pilot tubing from the gas valve if the pilot flame fails to light or ignites intermittently. If the tubing is worn or damaged, replace the tubing immediately. Confirm that the tubing firmly connects to the gas valve.