Barometric dampers contribute to stable heat and efficient fuel consumption by stabilizing flue draft -- in other words, regulating the flow of hot air in a chimney so that air flow is neither excessive nor lacking. As draft increases, barometric dampers automatically cause a flap to swing open wider, drawing "room air" into the flue and reducing draft. Thus, they prevent problems of high draft such as erratic burning and wasted fuel. Conversely, as draft reduces, the flap closes to reduce air, allowing the flow of hot air. The proper adjustment of barometric dampers is integral to their functioning.
Things You'll Need
- Manufacturer's specifications
Fire the unit at full rate on a typical cool day.
Locate on the barometric damper the draft gauge and weights. The weights should be adjusted according to manufacturer's specifications to obtain a standard draft gauge reading when the burner is operating at normal temperatures.
Adjust the damper weights until the draft gauge reads between the specifications supplied by the manufacturer. As draft increases above this level, damper doors will open, helping to keep draft constant.
- Photo Credit barometre image by anjocreatif from Fotolia.com
What Is Barometric Pressure?
Atmospheric pressure is the force exerted by air molecules as they bump into each other and surrounding surfaces, which translates to the...
How Does a Damper Work on an Oil Fired Furnace?
An oil-fired furnace is part of a forced-air heating system. This system burns oil in a combustion chamber to heat the air....
What is an Automatic Flue Damper?
Heating costs can be one of the largest costs associated with home ownership. A flue is an integral part of most furnace...
What Is a Barometric Damper?
A barometric damper is found in chimneys, stove pipes and furnaces. It is used to control the flow of air. Barometric dampers...
How to Install a Barometric Damper
Barometric dampers regulate the draft through fuel-burning devices, such as furnaces. They help to keep fuel burning at a steady rate in...
How to Use Zone Dampers
Zone dampers are manual or automatic doors located within ducts of a building's heating air conditioning and ventilation system. These doors may...