To determine a building’s energy efficiency, you can calculate heat losses from the structure. In a home or building, heat losses during winter can occur in various ways that include through walls, doors, windows, ceilings and floors. Because air leakage or infiltration through windows can cause heat losses that may increase your heating bill during winter, these calculations can be important factors to consider for your home’s energy efficiency. To calculate heat loss through windows, you can use a simple formula.
Things You'll Need
Calculate heat loss through windows by using the following formula:
HL = WA x U x (Del) T
In the formula, HL = heat loss, WA = the window area in meters squared, U= overall coefficient of heat transmission given in Watts/meter^2 deg Celsius (W/m^2 deg C) and (Del) T = the difference between the inside and outside air temperatures in degrees Celsius.
Utilize the formula in Step 1 to determine the heat loss through two windows that are 1.2 meters wide by 1.5 meters high and have a U-value of 2.5 W/m^2 deg C. The outside temperature is 0 degrees Celsius and the inside temperature is 18 degrees Celsius. Note that you can find the overall transmission coefficient value (U) for different materials from tables found readily online.
Multiply the width and height of one window to find the area as WA = 1.2 m x 1.5 m= 1.80 m^2
Subtract the outside temperature from the inside temperature to get the temperature difference (Del) T as 18 degrees C – 0 degrees C= 18 degrees C.
Calculate the heat loss through one window by using the equation HL = WA x U x (Del) T. Substitute into the formula the values for WA = 1.80 m^2 , U = 2.5 W/m ^2 deg C and (Del) T = 18 degrees C, you find that heat loss (HL) =1.80 m^2 x 2.5 W/m^2 deg C x 18 degrees C = 81 Watts
Multiply the heat loss (HL) found in Step 5 by two to get the total heat loss from both windows. The total heat loss is 2 x 81 Watts = 162 Watts.
Tips & Warnings
- The U-value, also called the thermal transmittance coefficient, is a measure of the heat flow through different materials.
- The U-value of 2.5 W/m^2 deg C, used in this example, is for a double-glazed wood frame window.
- You can use this same formula to calculate heat losses through walls and other surfaces.
- Photo Credit windows image by jimcox40 from Fotolia.com
How to Calculate Heat Gain
Heat gain is the amount of heat a room picks up on its own. Heat comes from a variety of locations, from...
How to Calculate for Heat Loss
Heat loss can be calculated manually or by using an automatic calculator or an online heat loss calculator. The transfer of heat...
How to Calculate Air Infiltration
Calculating the air infiltration of a building requires a complex set of operations, but the result provides keen insight into how the...
How to Do Heat Loss Calculations for HVAC Systems
Homeowners and HVAC technicians use heat loss calculations to determine the heating system size necessary to maintain the most comfortable indoor environment...