Electric water heaters are sometimes plumbed with piping constructed of two different materials, usually galvanized steel and copper. This can occur when new heaters are installed in homes with older plumbing systems. Joining the two pipes can create a phenomenon known as electrolysis. Electrolysis is a chemical reaction caused by the flow of electrical current between the dissimilar metals, and over time it may cause corrosive damage to the piping. Install a dielectric union to prevent electrolysis.
Things You'll Need
- Pipe sealing tape
- Pipe wrench
- Steel wool
- Propane torch
- Acid-free flux
- Lead-free solder
Wrap a layer of pipe sealing tape over the threads of the galvanized steel water pipe. Wind the tape in a clockwise direction, overlapping each turn approximately 50 percent.
Install the threaded end of the dielectric union onto the galvanized pipe. Turn the union clockwise and tighten with a pipe wrench.
Slide the union nut over the end of the copper pipe with the open threaded end facing out.
Score 2 inches of the end of the copper pipe with steel wool. Clean any existing burrs from the inside of the pipe lip with a reamer.
Install the brass union end onto the copper pipe. Be sure that the pipe is fully seated inside the brass end.
Sweat-solder the brass end to the copper pipe using a propane torch, acid-free flux and lead-free solder. Allow the pipe to cool.
Install the plastic insulator over the brass end of the union. Slide the union nut forward and turn it clockwise over the threaded union end on the galvanized steel pipe. Tighten using the pipe wrench.
Tips & Warnings
- Wear safety glasses when soldering and be sure to work in a well-ventilated space.
How to Install Galvanized Duct Pipe
Galvanized duct pipe, also known as stovepipe, is used to direct air in a central air conditioning system, vents dryer fumes and...
The Correct Installation of a Stainless Steel Pipe Union
Both stainless steel and gas pipe comes in various lengths, with threads at both ends. However, pipes of any size can be...
How to Install Unions in Copper Plumbing Pipe
The usual way to attach fittings to copper pipe is to sweat them, which means soldering with lead-free solder. Sweat connections are...
How to Install a Dielectric Nipple
Dielectric nipples are used to connect to dissimilar metals. Municipal, state and federal plumbing codes often prohibit the use of non-dielectric unions...