A water softener must not drain directly into a waste system because of the possibility of waste water flowing backward up the line. If this occurs, contaminated water could enter the water supply lines.
An air gap, which is essential to prevent backflow, is created by having the water softener empty into a floor drain, laundry sink or an outlet with a trap. The air gap should be two or more times the diameter of the drain line and at least 1.5 inches above the top of the receptacle.
The drain pipe can consists of either flexible or rigid material, as long as the end is secured in such a way to prevent it from becoming moved, dislodged or immersed in waste fluids.
Long garden hose is not recommended for a drain pipe because it may develop kinks or restrictions. If the drain empties into a sink, the sink should not be stoppered while the softener is regenerating.
How to Install a Water Softener Drain
A water softener's drain must not connect directly to a home's drainage system without an air gap between the end of the...
How to Prevent Backflow for a Floor Drain
Drains pipes are gravity based, meaning that the flow of water through a drain pipe is pulled to the lowest point in...
How to Install Water Pipes
Whether it is a remodel job or finishing a pre-built home, you will need to install water pipes. One type of tubing...
Proper Drainage for Garden Plants
Learn tips for how water should properly drain from flower pots, garden planters, pots, flower boxes and containers in this free video...