Remove the pump and associated piping from the well to repair a deep-well submersible pump. The pump is made up of a motor and an impeller. It may also have a check valve to prevent back-flow and a tail pipe attached below the pump. Start with a visual inspection and then apply electrical and mechanical tests to find which particular component is damaged. Once the damage is located, the entire damaged unit may have to be replaced or, if the damage is confined to a small part like a seal or a protective cover, that part may be replaced.
Things You'll Need
Turn off the power and lock out the breaker or disconnect switch. Remove the well cap and shine the flashlight into the shaft. You'll have to disconnect the pitless adapter and pull up the pipe, electric cable and pump. Look for a pipe, chain or rope that was used to lower the pump into place. Use it to raise the pump and pipe, and make the pitless adapter slide out of its holder. Otherwise, place a chain under the pipe elbow leading to the pitless adapter and haul up the pipe. Small wells with pumps less than 1/2 horsepower, pipes 1/2 inch or less in diameter and less than 100 feet long can be lifted out by hand. Larger units are too heavy and need a tripod and winch to haul out.
Inspect the pump visually. Check for wetness on the pump and pipe string to make sure the pump is actually submerged. If not, you will have to add pipe to situate the pump deeper in the well or drill the well itself deeper.
Check for obvious damage. There may be mechanical damage caused by debris in the well. Such damage can often be repaired by replacing the cover or casing of the pump. The check valve or tail pipe may be clogged and can be freed.
Check for electrical motor damage. Remove the motor cover where the cable enters the motor. One of the cable wires connects to the starting capacitor. Switch the multimeter to resistance testing and connect across the capacitor. The needle should jump. If it doesn't or if the meter reads zero resistance, the capacitor must be replaced.
Check the motor resistance. An open circuit means that there is a bad connection or a winding, or connection has burned through. A zero resistance means the motor has shorted out. In either case, the motor must be replaced.
Check for mechanical problems with the impeller. Use a screwdriver to turn the motor to see if the impeller turns freely. If not, open the impeller casing and remove the obstructions. Check the impeller for cracks and check the seals at either end for wear or gaps. If there is mechanical damage, the impeller itself or the whole impeller unit must be replaced.
Reassemble the repaired unit and lower the pump and pipe back into the well. Make sure the pitless adapter engages when the pump is in position. Close the well cover.
- Photo Credit Jupiterimages/Goodshoot/Getty Images
How to Install a Well Water Submersible Pump
When your submersible well pump goes out and you suddenly have no water, you realize how much your life depends on the...
How to Select a Submersible Water Well Pump
A submersible pump is used for wells that are relatively deep and require a lot of pumping power. They go into the...
How to Remove Sulfur Smell From Well Water
Sulfur smells in well water come from hydrogen sulfide. Removal usually requires the installation of a filtration system.
How to Remove Submersible Well Pump
Learn the symptoms and causes of pump failure, and how to remove a submersible pump from a well by hand, or with...
How to Build a Wood Pole & Rope Lifting Tripod
A tripod made from wood poles, with a rope and pulley attached, helps you lift weights higher or heavier than you could...
How to Repair Leakage in a Deep Vein
Veins contain one-way flap valves that help blood return to the heart. When valves fail, blood pools in the veins and they...
How to Pump Water From a Deep Well
Pumping water from a deep well requires a deep well jet pump. Deep well pumps are cost efficient and require little maintenance...
How to Troubleshoot Deep Well Pump Systems
Deep well pump systems are designed for wells more than 25 feet deep. A pipe leading from the impeller housing pushes water...
How Do I Replace a Deep Well Pump?
Deep well pumps spend their useful service life submerged under a hundred feet of water or more, pushing it to the surface...