A properly installed reverse osmosis (RO) unit will give you water almost as pure as distillation. It performs this task by passing filtered water across a semipermeable membrane that excludes anything larger than a water molecule. Wastewater is routed away from the filter into the drain. The purified water is stored in a pressurized holding tank until needed. If your unit stops working, try the steps below.
Check the Water Supply
Check your pressure. The RO unit needs about 40 pounds of pressure to operate correctly. Many older water wells were set up to operate below this pressure. If you have a well or low water pressure, you might need to install a booster pump for the unit to operate efficiently.
Inspect the water-supply valve, ensuring it is in the fully-open position. If it is clogged or only partially open, the RO unit might not build up sufficient water pressure to operate.
Inspect the unit’s supply lines. A kinked line will restrict water flow and prevent proper operation.
Inspect the Storage Tank
Open the unit’s tap and allow the water to run until the tank is empty. Use a pressure gauge to check the air pressure in the tank. The pressure in an empty tank should be eight pounds. If the pressure in the tank is too high, water will be unable to enter from the filters. If the pressure is too low, the water inside the tank will not flow to the faucet.
Replace the Filters
Close the water-supply valve and open the RO faucet. Allow the tank to drain. Unscrew both the pre- and post-filter housings. Replace the old filters and screw both units back in place. These filters should be replaced at regular intervals to prevent damage to the delicate membrane of the RO filter.
After replacing the two filters, close the RO faucet and open the water-supply valve. After three hours, check the faucet. If you have gone through all the above steps and still fail to get water out of the faucet, you will need to replace the RO membrane.
Replace the RO Filter
Close the water-supply valve. Open the faucet and drain the storage tank. Close the faucet after the tank has drained. Unscrew the filter housing and remove the RO membrane. Wash the inside of the filter housing with warm, soapy water. Rinse it thoroughly. Put on a pair of clean rubber gloves to handle the new RO membrane. Bacteria from your hands can contaminate the filter membrane. Insert the new RO membrane into the housing and replace the housing on the filtration unit.
Open the water-supply valve. After eight hours, open the faucet and allow the tank to drain completely. This step is necessary to wash out the preservatives that were inside the new membrane. Close the faucet. Once the tank has filled again, the unit will be ready to use.
- Photo Credit Jupiterimages/Pixland/Getty Images
Why Does My Reverse Osmosis System Gurgle?
An intermittent gurgling sound from your reverse osmosis water purification system is fairly common, especially in new installations. It’s caused by air...
How to Install a Reverse Osmosis System
I have installed two Reverse Osmosis Systems in my last two homes. The first one was to filter our very, very hard...
How to Clean a Reverse Osmosis Water System Tank
The tank on your reverse osmosis water purifier is designed to hold two or more gallons of clean water in reserve in...
How to Troubleshoot a Reverse Osmosis System
When troubleshooting a reverse osmosis water system, it’s important to understand what you may be looking at as the cause of the...
How to Drain a Reverse Osmosis Water Storage Tank
Reverse osmosis, or RO, systems are a type of water filtration system that moves water through a set of membranes to remove...
How to Troubleshoot a GE Reverse Osmosis
GE's reverse osmosis (RO) drinking water treatment systems remove large particles from your household water supply through a chemical process that filters...