Virginia and many other states have adopted numerous international building and safety codes regulating plumbing, property maintenance and those for the design and installation of natural gas and propane lines. The International Fire Code and the National Fuel Gas Code, (NFPA 54), of the National Fire Prevention Association, are also Virginia standards. All work in conjunction with the installation, operation and maintenance of gas piping must be performed in accordance with these codes. This ensures the highest level of building safety for communities.
Permits for Propane Tanks
Most propane tanks are 500 or 1000 gallons in size for residential use. All tanks, greater than 500 gallons, must be registered and meet requirements of the State Water Control Board. Permits must be obtained for above and below ground propane tanks. When a home is built, the company installing the septic system often digs the hole for an underground storage tank. Cooperation is necessary to insure the septic system will be placed where it's not driven over or damaged by propane delivery tanks.
Propane Tank Installation
The tank installer places it the required distance from the structure and installation is completed, following regulations. The propane gas line runs from the tank to a gas line stub outside the house. This gas connection pipe extends out through a basement wall a maximum of 2 inches with a minimum height of 18 inches above grade. This connection pipe must be threaded. Copper line cannot be used as a main gas connection line through a concrete wall. The gas connection can't be within 3 feet of a venting window, door or within 5 feet of an ignition source.
Propane Tank Gauge
Most tanks have a gauge located under the lid to show the amount of fuel it contains. Tanks are filled to 80 percent of capacity to allow expansion of the liquid gas. The propane tank sits on a concrete pad, and the line is placed in a trench dug according to code. A required pressure test is completed by the installer to ensure pressure meets the requirements and that there are no leaks.
Installing Gas Appliances and Equipment
Propane or gas appliances must be installed by a service representative. Required clearance distances between a gas appliance and combustible walls represent minimum requirements for safe operation. This is particularly important when installing a gas fireplace. Permits and inspection are required for all vented gas space heating units, including combo-heaters, which are a combination water and space heater. Shut-off valves must be placed at every appliance hookup.
Vents must be properly sized for the appliance, made of approved materials and secured according to code. Duct tape or foil tape shouldn't be used to seal up vent pipes that come apart. Deteriorating vent pipes should be replaced. Care must be taken when installing vents through a wall or ceiling to avoid danger from combustible materials. Fire-stop spacers must be used that ensure a hot vent will not shift and touch a wooden joist or combustible material used in the building's construction.
- Photo Credit gas shut-off valve image by enens from Fotolia.com passeport image by Loic LUCIDE from Fotolia.com house image by kruszek from Fotolia.com pressure-gauge image by Dusan Radivojevic from Fotolia.com laundry image by timur1970 from Fotolia.com hot tap image by pncphotos from Fotolia.com
How to Install a Propane Tank
Propane-fueled grills are among the most common grills on the commercial market. These grills require a tank filled with liquid propane to...
How to Install a Propane Line for a Stove
Many people prefer to cook on a gas stove as it allows for more precise temperature control of the burners for sautéing...
Maryland Propane Tank Laws
Homeowners living in rural areas and even some in larger cities may have propane tanks that provide a fuel source for the...
Requirements for the Clearance Around Propane Tanks
Homeowners who decide to install a propane tank on their property need to be aware of a few safety guidelines. The National...