Septic system alarms alert the homeowner when an imminent sewage back-up is likely. Inside the septic tank, a float switch tethered to a fixed position in the tank floats up and down with the liquid level. When the liquid level gets too high, a switch inside the float closes the alarm circuit, activating the alarm. Septic system installers bury two wires from the house to a new septic tank. One wire provides power to the pump, while the other wire is reserved for the septic pump alarm circuit. Septic system installers install the alarm float switch to the inside of the septic tank. The wiring of the float switch to the alarm circuit remains the homeowner's responsibility.
Things You'll Need
- Septic alarm with mounting hardware
- Junction box with cover
- Electrical conduit
- Septic alarm float
- Two wire nuts for 12 AWG wire
At the Tank
Locate the alarm float wires and the alarm circuit wires running to the house. (They should have a label.)
Push the wires through the electrical conduit and into the junction box.
Hold the bare ends of the black wires together and insert the pair into a wire nut, twisting it until it is tight. Repeat with the white wire and the other wire from the float switch.
Press all the wiring into the junction box and screw the cover into place.
In The Home
Locate the alarm in a high traffic area close to the incoming septic tank alarm wires and an electrical plug-in.
Insert the mounting screws through the mounting holes in the alarm's housing and screw into the wall.
Connect the black wire from the septic tank alarm circuit to the positive terminal on the alarm. Connect the white wire to the negative terminal.
Screw down the terminal lugs until they are snug.
Insert the power plug for the alarm into the power receptacle.
Tips & Warnings
- Test wire connections by gently pulling on them.
- Test the alarm by physically lifting the alarm floats to its upright position. If installed correctly, the alarm will sound.
- A junction box must not have a direct conduit to the septic tank. Gases from the septic tank could enter the junction box and create an explosive hazard.
- Photo Credit Jupiterimages/Creatas/Getty Images
How to Wire a Septic System
The majority of septic systems rely on gravity to move processed waste water from the tank to the drain field lines. In...
How to Install a Holding Tank System for a Septic
Holding tank septic systems are designed for temporary use only. The holding system retains the waste until it can be pumped out....
How to Install a Septic Pump System
For homeowners without access to municipal sewage systems, septic tanks treat and dispose of waste products. Homeowners are responsible for the maintenance...
How to Troubleshoot a Septic System Pump
It all rolls downhill--that is, until the septic pump stops working. Then, it can start to overflow and even back up into...
How to Troubleshoot a Tank Alert Alarm
A tank alert alarm is an electronic system that monitors liquid levels in sump pump basins, holding tanks, sewage and other non-potable...
How to Install a Septic Tank Switch
Septic tanks with pumps rely on a float switch within the tank to sense the liquid level in the tank. As the...
How to Troubleshoot Septic Float Switches
If your septic system uses a pump to remove wastewater from the tank to a drain field, your system will include a...
Troubleshooting a Sticking Float in a Septic Tank
Septic systems utilize float switches to turn on alarms and stop and start effluent pumps. Float switches that are improperly or carelessly...