Air flow must be balanced in a house to provide efficient heating and cooling. A system of return ducts to send "used" air from inside the house back to the heating/cooling unit must be of equal capacity with the "conditioned" air generated from the unit. Air flow is measured in cubic feet per minute coming from the unit; the return system should send that same air flow back. Ductwork is installed during construction in new houses and when heating/cooling is added or expanded in older ones. Any changes may require return modifications.
Things You'll Need
- Tape measure
- Utility knife
- Crow bar
- Reciprocal saw
- 2-by-4-inch framing boards (optional)
- Screw gun
- New return air filter frame
- Flexible duct
- Heat-resistant tape
- Tin snips
Locate all existing return duct openings. An ideal system would have a return in every room where there is a supply vent, but ideals are rarely achieved; there usually are fewer returns. Return ducts are in a floor or at floor level on an inside wall. Supply ducts are on outside walls. Measure the size of return openings with a tape measure. Count and measure the supply ducts. That should give you a difference between supply and return duct capacity.
Modify an existing return opening vertically; a 14-by-20-inch return can be expanded to 24, 28 or 30 inches high. Remove the metal air filter frame and cut wallboard to the desired height by cutting it with a utility knife and peeling off with a crow bar. Replace the flexduct from the return opening to the unit with the larger size. Seal seams with heat-resistant tape. Install new framing of the right size to hold the air filter by screwing it to the studs on each side..
Enlarge the return horizontally if a vertical expansion is not possible. Determine a size; return frames and filters come in dimensions up to 30 inches, but 28 inches will fit a space between wall studs. Mark the wall where the top of the new frame will go. Remove the wallboard at that point, to reveal three studs. Cut the center stud with a reciprocal saw at the top of the opening. Cut a 2-by-4-inch header and screw it to the two outside studs. Cut and install short 2-by-4-inch studs to go from the header te the wall base plate. Remove old ductwork and install new duct of the proper size, sealing seams with heat-resistant tape. Screw a new filter frame to the studs on each side.
What Is the Difference Between Range & Downdraft Hoods?
Updraft range hoods and downdraft range hoods serve the same function: to draw cooking smells, steam and grease vapor out of your...
How to Install a Cold Air Return Duct Between Studs
Running a metal cold air return duct between studs requires knowledge of both HVAC systems and the components involved in framing. First,...
How to Install a Duct Vent Fresh Air Intake for a Furnace
With today's homes being built increasingly airtight, it is becoming essential to bring fresh air into the home mechanically. Without fresh air,...
How to Install a Return Air Duct
A return air duct is what carries air back to the furnace after it is dispensed throughout the home through the supply...
How to Determine Your Heating Air Duct Requirements
The heating and air conditioning system is an important consideration to keep in mind when building a new house. Installing the ductwork...
How to Extend Ductwork
Ducts are the branches of the heating and cooling system of your home that provide the airflow from the main blower unit...
How to Increase the Capacity in an Existing Return Air Duct
Air flow to an air conditioning or heating system is critical for proper operation. An air-starved unit will not only have poor...