A 240-volt circuit has two hot wires that together make up 240 volts; each wire carries 120 volts. There is also a ground wire; it will be colored green or copper. In a 240-volt circuit there is no neutral wire. You can wire a 240-volt circuit to provide both 120 and 240 volts. For a generator 240-volt connection it is best to wire it direct and with only 240 capabilities. The generator is an additional power source or a backup source. You want to keep the wiring dedicated to the need of the generator since its purpose is for additional or emergency power.
Things You'll Need
- Volt meter
- Flathead screwdriver
- 8/3 cable
- Stripper tool
- 40-amp double pole breaker
Turn off the main power supply leading into the house. Use a volt meter to test the termination of electricity into the breaker panel. Do not work in the breaker panel if electricity is still flowing.
Strip the 8/3 cable a 1/2 inch from the end exposing the wires. Use a stripper tool for a cleaner cut. Strip the ends of these three wires a 1/2 inch as well.
Screw the two black wires to the circuit breaker The circuit breaker has two screws that each hold one black wire. Insert the wires fully by pushing them into the terminal and tighten the screw securely.
Install the breaker into the service panel. Set the breaker in the housing in the service panel where you want the circuit to reside. Rock the circuit back and forth: inserting the tabbed end of the breaker into the housing first and then snapping the rest of the breaker over the hot bus bar.
Look at the double pole breaker to make sure it fits snug. The breaker for a 240-volt installation is a double pole breaker because of the two 120-volt hot wires totaling 240 volts.
Thread the ground wire through the ground bar and run the wire to the end of the 240-volt receptacle in the breaker box. Screw the ground wire to the end of the 240-volt receptacle.
Run the 8/3 cable to the outlet you want the generator to plug in to. Attach the two black wires to the screws that aren't colored and then attach the ground wire to the green screw.
Attach the outlet to the wall after the 8/3 cable is secured. Go to the main power supply and turn it on. Next push the breaker to the "On" position. Plug the generator into the outlet and start it up.
Tips & Warnings
- In order to comply with code, the two line voltage wires feeding into the 220-volt circuit need to be the same color black or red. You can mark the wires with tape if necessary.
- An 8/3 cable works for a 40-amp breaker.
- De-energizing of the main panel doesn't always occur by shutting off breakers. Use a volt meter to test the termination of electricity. Death can occur from electric shock.
- Photo Credit Jupiterimages/Photos.com/Getty Images
How to Wire a 240 Volt Circuit
Wiring a 240-volt circuit is a simple matter if you know a few basic steps and take some precautions for safety. A...
How to Wire a 240 Volt Portable Generator Plug
The standard 240-volt portable-generator plug is a four-wire NEMA L14-30 plug that can be found in most hardware stores. The four wires...
How Do I Convert 12 Volt DC to 120 Volt AC?
Converting 12 volt DC power to 120 volt AC power is generally a two-step process. You have to first convert the 12...
How to Get From 120 Volt to 240 Volt
In the United States, electrical outlets provide 120 volts of electricity. However, certain kinds of electrical devices use 240 volts instead. To...
How to Make a 240-Volt Cord for a Generator
Generators produce electricity; they also produce a lot of noise and poisonous carbon monoxide fumes. For safety reasons they are often located...
How to Wire a Transfer Switch to a Circuit Breaker Panel
Having a generator to provide power to your home can be a benefit if you live in an area that is prone...
How to Use the 240/120 Volt Receptacle on a Generator
Portable generators with 120/240V capability typically include a four-prong electrical receptacle for powering 240V appliances, as well as multiple 3-prong receptacles that...
How to Rewire a 3 Phase Generator to a Single Phase
If you have three-phase generator but wish to use it to power single-phase devices, rewiring is generally very difficult. A much simpler...