Extending or expanding an electrical circuit in your home will probably require you to add wiring. Romex is a trade name for non-metallic sheathed cable and consists of two or more insulated conductors within a plastic sheath. Usually the sheathed cable includes a bare ground conductor. Extending Romex past a receptacle or fixture means you'll have to tie into an existing circuit and run the cable to the new fixture, outlet or switch location. Properly extending the Romex is important to meet National Electric Code Requirements.
Things You'll Need
- No-contact voltage tester
- Sheathed cable stripper
- Sheathed cable staples
- Long nose pliers
- Lineman's pliers
- Wire nuts
Extending From Receptacles
Turn the power off at the circuit breaker to the Romex circuit you will be extending and test it to be sure it is off with the no-contact voltage tester. Bring the probe close to the Romex cable already in the receptacle box and if the light stays off, the circuit is off.
Strip 8 inches of sheathing from the end of the cable with the sheathing strippers, remove the paper wrappings and insert the cable into the plastic wiring box. Staple the new Romex cable to the stud within 8 inches of where it enters the box.
Strip 3/4 inches of insulation from each of the two insulated wires. Bend the stripped portion of the wires 180 degrees with the long nose pliers. Do the same to the bare ground wire.
Loosen the green ground terminal with a screwdriver. Place the ground wire on the terminal screw so the bend wraps around the screw clockwise. Tighten the screw firmly.
Loosen the two empty side terminal screws and place the white wire around the silver terminal screw with the turn going clockwise around the screw. Put the black wire on the brass terminal screw the same way and tighten both screws. After you replace the receptacle and cover plate, the new Romex circuit is ready to be connected at the other end, extending the circuit.
Find a junction box with the Romex cable circuit you wish extend inside. Turn off power to circuit you are working on at the circuit breaker and test it to be sure it is off with the no-contact voltage tester by bringing the probe close to the Romex cable you will be splicing to.
Remove the wire nuts on the black, white and bare wires. Strip 8 inches of sheathing from the Romex cable and insert the cable into the box. Strip 1 inch of insulation from ends of the new wires.
Twist the new bare ground wire around the existing bare ground wire connection with the lineman's pliers and replace the wire nut on the connection, twisting it on until the wire nut is on tight. Hand tighten the nut --- do not use pliers.
Twist the white wire end around the existing white wire connection with the lineman's pliers. Replace the wire nut and be certain no bare copper shows after the wire nut is in place.
Twist the black wire end around the existing black wire connection with the lineman's pliers. Replace the wire nut and be certain no bare copper shows after the wire nut is in place. After you replace the junction box cover plate, the new Romex circuit is ready to be connected at the other end, extending the circuit.
Tips & Warnings
- You might need larger wire nuts when connecting to an existing Romex cable in a junction box.
- When splicing into a connection with more than two or three wires, it is usually better to cut the existing twisted ends off, strip new ones and twist all the wires together again instead of trying to wrap the new wire around the old connection.
- Always work with the circuit breaker turned off. Never work on a live circuit and always test to be sure it is off.
- "Basic Wiring"; Time Life Books; 1994
- Photo Credit electrical wires image by jimcox40 from Fotolia.com
How to Splice a Romex
Nonmetallic sheath (NM) cable is often referred to as ROMEX®, a registered trademark of the Southwire Company. NM cable is the cable...
How to Recognize an Old Romex
Romex is the brand name for a type of non-metallic electrical wiring installed inside the walls of a new home during construction....
How to Add Romex to an Existing Line
Romex is a trademark brand of the Southwire Corporation. The name "Romex" refers to non-metallic sheathed cables originally produced by the Rome...
How to Size Romex Cable in an EMT Conduit
Sizing electrical metallic tubing (EMT) conduit depends on the gauge of the wires you are running inside the conduit and the amount...