Every building that uses forced hot air for heating will have cold air return vents. They do precisely what the name implies: return cold air from registers to the furnace so that it will run properly. Return vents also provide air circulation. Return vents are necessary to prevent pressure buildup that may lead to illness, help prevent mold and mildew, and help prevent deterioration of the building structure. When warm air is forced into a room it replaces the cooler air. The cooler air must be pushed out of the room otherwise it becomes over-pressured. The cooler air is forced into the return vent back to the furnace where it is reheated, and the cycle begins again.
Examine your home heating system. It is important to understand the space that you're heating. The output of air must equal the input of air. If the input into the furnace is less than the output, this will cause pressure in the house and a possible backup of dangerous fumes. If the return vents are lacking in proper spacing, the air will travel to the furnace through rooms and down stairways. This creates a draft which defeats the purpose of a forced air system.
Place your cold air return vents on the inside walls of buildings at the lowest point. The return vent pulls cold air from the bottom of the room and returns it to the furnace to be reheated and returned as warm air.
Unlike supply vents, return vents do not need to be cased in metal. They can be placed into staircase cavities, stacked closets that run one on top of the other, or in stud cavities in the wall. Where one return vent serves an entire zone, air space should be provided under doors so that when they are closed the registers can still draw air without pulling against the furnace (which causes negative pressure in the home).
Place the vent at least 10 feet away from a thermostat, because the cold air draft may cause incorrect temperature readings.
Use exhaust fans to expel the air from kitchens and bathrooms because of the high moisture content. Follow municipal building codes regarding vents in these rooms.
Tips & Warnings
- It is ideal to have one return vent in each room that has a heating register. However, it is also common to have one return vent per heated area (ie. living room and dining area combined if within the same zone).
- Consult a professional heating contractor for more information on achieving a properly balanced hot air heating system..
- Photo Credit Mel Curtis/Photodisc/Getty Images
How to Install a Cold Air Return Duct Between Studs
Running a metal cold air return duct between studs requires knowledge of both HVAC systems and the components involved in framing. First,...
How to Install a Return Air Duct
A return air duct is what carries air back to the furnace after it is dispensed throughout the home through the supply...
How to Clean In-Floor Air Return Vents
An in-floor air return vent is the location where air is sucked into a home's central air conditioning or heating system. It...
How to Size an Air Conditioner Return Air Duct
Properly sizing and installing your air conditioning system are important in making sure your air conditioner operates efficiently, according to the U.S....
How to Position a Thermostat
Thermostats are rarely ever a simple mechanical liquid mercury device attached to a thermometer anymore. Even low-cost thermostats tend to be programmable...
The Air Return Size for a Furnace
Sizing ducts for a heating system is a complex task. It involves the heat output of the unit, measured in British Thermal...
Should a Thermostat Be Near a Return?
A home's thermostat is what monitors the ambient temperature and signals to the HVAC system a need for heating or cooling. Modern...
Can I Cover a Cold Air Return Vent?
A furnace is basically a recirculating air pump; it draws cool air from all the rooms in your house that have a...