Flushing a central heating system can often be necessary task, particularly when the system is producing rust or sludge, a tell-tale sign that your system is operating inefficiently. Flushing may also be needed if a new system or radiator has been installed.
Things You'll Need
- Hose pipe
- Jubilee clip
- Radiator key
- Wooden rod (must be same length as header tank)
- Stiff wire
Turn off all the power that controls the heating system. Any gas or electricity connected to the boiler, as well as control switches on the boiler, should also be turned off. Locate the feed/expansion tank, also known as the header tank, in the loft. It will be the smaller of the two tanks. The tank's water supply must either be turned off, or the ball valve must be blocked. Make sure that there is no water in the ball. A leaky ball can make the heating system less efficient, and would need to be replaced. Stop water from entering the tank during draining by laying a piece of wood across the tank, lifting the valve onto it and tying it to the wood so it will remain shut off.
Connect the drain cock, usually located at the lowest part of the pipework, to a hose secured by a jubilee clip. The hose should be run outside the house, but avoid roads, sidewalks or other pavement that have the potential for accidents. Use a pair of pliers to open the drain valve.
Open up all the bleed valves on all radiators in order to speed up the flushing process. Open up the highest level valves first and work down to the lowest. Opening the lower valves too soon can cause water to push out from the valves instead of sucking in air.
Check the system to see if it is fully flushed once water has stopped running from the hose. Air in the system may have prevented some water from draining. If this is the case, loosen the ball cock in the header tank so about 6 inches of water can come in. This water should drain from the hose in a few seconds. If an air lock is stopping the water from draining, connect the hose's other end to a cold tap and shoot water into the blocked radiator.
Close all the bleed valves and the drain cock that have been opened. Release the ballcock in the feed/expansion tank to let it refill. Start bleeding the lower level radiators and work upward once the tank is full. Check all valves to make sure they are shut tightly.
Turn on or relight the boiler. You may hear a knocking noise as the result of air expanding in the system. Stabilize the system by bleeding the radiators again and checking the system for leaks.
Tips & Warnings
- Clear or dirty gray water is a sign that your central heating system has been properly flushed. Dirty black or rusty-colored water indicates sludge or corrosion.
- You can only follow these steps in flushing your central heating system if it is a standard venting system. If it is a sealed combination boiler system or if you are not sure which type you have, let a professional flush your system instead.
Problems With Central Heating Systems
The Home Tips website describes several types of central heating systems. A ducted air system uses an electric furnace to heat air,...
How to Troubleshoot a Home Central Heat & A/C System
When it comes to central heating and cooling, home owners are usually beset with a myriad of issues. Otherwise known as an...
How to Flush a Heating System
Flushing a heating system is a chore people tend to put off until the last minute. Instead, make it part of your...
How to Bleed a Central Heating System
When air becomes trapped in your central heating system, it can noticeably reduce the thermal output of your radiators. Air can get...
How to Flush an Air Conditioning System
If a vehicle's air conditioning system is not operating correctly, sometimes flushing the entire system will improve its efficiency. Flushing the air...
How to Install Central Heating Systems
Central heating allows you to maintain a comfortable temperature in your house with only slight variations in the temperature from room to...
How to Flush out the Drain on an Air-Conditioning Unit
Water damage inside your home can be extremely costly to repair. If you have central air-conditioning it is important to check the...