Running a branch circuit for a 240-volt baseboard heater with a double pole across the line thermostat is a relatively simple but labor-intensive project. If you will be installing the baseboard heat during new construction, the walls will still be open, and running the wire will be quick and easy. If you are installing baseboard heat to a finished room, you will have to fish the cable through finished walls and floors while causing minimal disruption to the structure.
Things You'll Need
- 3-conductor (with ground) non-metallic sheathed cable
- Cable connectors
- 2-pole, 240-volt circuit breaker
- "Old Work" device box
- 2-pole thermostat
- Digital multimeter
- 3/8-inch, battery-powered drill/driver
- Spade bits
- Electronic stud finder
- Electrician's screwdrivers
- Razor knife
- Lineman's pliers or electrician's pliers
- Diagonal pliers or wire cutters
- Wire strippers
- Needle-nose pliers
- Yellow wire nuts
- Black plastic electrical tape
- National Electric Code ratings
Calculate the size/rating circuit breaker required by multiplying the heater's FLA, ,or full load amperes, by 1.25. The National Electric Code, or NEC, classifies baseboard heat as a "continuous duty load," which can be expected to pull full amps continuously for three hours or more. Breakers serving continuous duty loads must be rated not less than 125 percent of the full-load current.
Compare the calculated over-current protection device (OCPD) rating with the standard ratings given in NEC Article 240.6(A). If the calculated rating falls between two of these standard values, use the next higher rated CB.
Calculate the branch circuit conductor's required Ampacity. Conductor "Ampacity," like the OCPD rating for a continuous duty load, should not be less than 125 percent of the full-load current.
Compare the computed minimum required branch circuit conductor Ampacity to the standard Ampacity given in NEC Article 310.15 and NEC Table 310.16 using the 140-degree Fahrenheit column. If the required Ampacity falls between two standard ratings, use the wire size for the higher rating.
Locate the device box for the thermostat on the opposite wall from the baseboard heater to ensure even heating of the room. Mount the thermostat's device box 46 inches above the finished floor line.
Route the cable from the thermostat location to the baseboard heat unit and from the thermostat location to the service panel.
At the baseboard heater, secure the cable in place and strip off the outer jacket so that there's 6 inches of free conductors in the splice box.
Strip ¾-inches of insulation from each of the conductors and splice the red and the black conductors exiting the cable to their counterpart on the heater.
Connect the bare copper grounding conductor to the heater's frame. Depending on the unit's design, this may be accomplished with a green grounding screw, a grounding pigtail, a metal clip or some other method.
The white, neutral conductor may or may not be used depending on heater design. Check the wiring diagram that came with the baseboard heat unit.
Install both cables into the thermostat's device box and strip the jacket off them so 6 inches of free conductors are available in the box and secure the box in the wall by pulling the box's wings up against the inside of the finished wall.
Strip ¾-inches from each of the conductors and splice the two white neutral conductors together.
Using a 6-inch length of bare copper wire, make a pigtail splice with the two bare copper grounding conductors in the device box.
Using the needle-nose pliers, form loops in the free ends of all the conductors in the box, in preparation for connecting them to the thermostat.
Install the line thermostat. Connect the red and black wires from the service panel to the "line " side of the line thermostat and the heater cable to the "load" side of the thermostat. Connect the grounding pigtail to the green grounding screw.
Install the 2-Pole CB in the service panel connecting the red and black wires to the breaker's terminals and running the white neutral conductor to the panel's neutral and the bare grounding conductors to the panel's grounding bar.
- Photo Credit Thinkstock Images/Comstock/Getty Images
How to Wire Electric Baseboard Heaters
Baseboard heaters are a fast and cheap way to supplement the heat in your house. The number you need depends on how...
How to Wire Multiple Baseboard Heaters
Baseboard heaters are generally used in rooms that may be far from the central heating source. These electric heaters are positioned under...
How to Install a Line Voltage Thermostat
Line voltage thermostats control electrical power to heating and cooling devices. The two basic types of line voltage thermostats are single-pole and...
How to Wire a Base Board Heater
Baseboard heaters are available with two voltage ratings: 120V and 240V. The 240 Volt baseboard heater is the most common and energy...
How to Wire a 240V Thermostat
Thermostats designed to operate 240 volts heaters have two "hot" terminals, each accepting one standard 120 volt connection. Electric baseboard or wall...
How to Wire a 240V Electric Baseboard Heater
There are numerous ways to wire an electric baseboard heater, depending on your heating configuration and whether you are connecting a single-pole...