If you are trying to replace a submersible well pump first read my article about removing submersible well pump, it's in the the resource section of this article. I broke it up into two articles because it's a lot of information.
Things You'll Need
- New pump (Identical to old pump or upgrade if unhappy with originals performance)
- Check valve (same as original)
- Tripod and pulley as discussed in article on "submersible pump removal" in resource section
- Polyethylene pipe (same diameter as original pipe)
- Water proof electrical splice kits (2)
Once you have the old pump out and have determined it needs replacing you can see the type and model pump that you need to buy. Wire the old pump directly to power source once you have it out to make sure it needs replacing and that the problem is not in the wire that ran down in to the well.
If you determine that the water level is still the same as before ( I'm going to write an article on how to determine this in the future) measure the wire or safety rope that you used to pull the pump out to determine the length of the new pipe if it needs replacing, more than likely this is the case as the pvc pipe used on most installations is hard not to break on removal but the polyethylene pipe for the new pump installation is not expensive. When measuring for length of replacement pipe do this before you buy the pipe so you can by a roll big enough for the entire length, you can't come up short here and you can't splice sections together.
Take the polyethylene pipe and unroll it on a sunny day. The sun will relax the kinks and allow the pipe to soften slightly allowing much easier handling. Tape the wiring that was attached to the original pump, assuming it doesn't need replacing (it normally wouldn't but a well company would try to sell you new wire) to the polyethylene pipe at eight to ten foot intervals for its entire length ( typically 150-250 feet for a well)
Make sure you have the circuit breaker off to the wire that leads to the well, test it to be sure.
Take the waterproof electrical splice kit that is appropriate for your gauge wire and splice the wire leads from the end of the wire that is now taped to your polyethylene pipe to the leads on the new well pump. Before you put the pump back down the well test it by turning the circuit breaker on and temporarily connecting the well wire to the wire that comes from your house. I put the pump in a barrel full of water so I could test it and not damage it, you should see a jet of water shooting out from the barrel if it's working properly.
Attach the pump to the polyethylene pipe with whatever brass fitting is appropriate and replace the check valve , as well, which is above the pump, unless it is a pump that has one built in. It's probably a safe bet to duplicate the set up that was used on the original well pump.
To lower well pump you have to use the pulley and tripod assembly discussed in well pump removal article, but first you need to tie the safety rope attached to old pump to new pump ( unless damaged than replace) and thread it through pulley and attach other end to truck or other vehicle to anchor it. Back the vehicle up as you lower well pump/hose/wire assembly down the well hole.
As you near the depth required, you have to attach the pitless adapter to the end of the polyethylene pipe by hose clamps or whatever means are appropriate. Line up the pitless adapter, as you lower it carefully, with the the slot it slides into on the inside of well casing until seated fully. Using a rubber mallet to tap the pitless adapter into its slot can make it easier to assemble.
Now take the other waterproof splice kit and splice the power wire from your house to the wire that is connected to the pump. Test everything now before you close well cap and that should do it- it's a lot of work but it can save you thousands of dollars and if you're a very handy confident diy'er it can be done.
Tips & Warnings
- Make sure you have safety rope anchored at all times to vehicle or something sturdy because if pump is dropped while lowering or raising the safety rope could break dropping the pump all the way down- big problem
- Another way to determine the length of the new pipe would be to lower a rope down the well noting the distance down until the rope shows a water line, measure this distance than ask your original installer how far below the water line the pump should set.
- Talk to your original installer, if you don't know that info look on the well cap it might be there, they are normally helpful with any questions you might have and they might sell you a new pump at wholesale cost, which is what they did for me
Submersible Well Pump Lifespan
There are several factors that may impact the lifespan of a submersible well water pump, including the pump's duty cycle, size and...
How to Install a Well Water Submersible Pump
When your submersible well pump goes out and you suddenly have no water, you realize how much your life depends on the...
How to Select a Submersible Water Well Pump
A submersible pump is used for wells that are relatively deep and require a lot of pumping power. They go into the...
How to Install a Water Well Pump
Installing or replacing a submersible water well pump is not a difficult undertaking for the motivated do-it-yourselfer. Installing the pump yourself will...
How to Repair a Deep Well Submersible Pump
Remove the pump and associated piping from the well to repair a deep-well submersible pump. The pump is made up of a...
How to Size a Submersible Well Pump
Submersible well pumps are seated beneath the water level in the well. These pumps are considered to last for a long time...
How to Wire Deep Well Pumps
A deep well's pump typically pulls water from a 50 to 300-feet deep hole. The pump often hangs about 10 feet off...