Depending on what your HVAC (heating, ventilating and air conditioning) system does, it may have two, four, five, six or seven thermostat wires. Two-wire systems are heating only, four-wire systems are heating and air conditioning, five-wire systems are for thermostats that receive their power from the HVAC system, six-wire systems have two stages of heat and seven-wire systems have two stages of heating and cooling. The seven-wire system is most efficient because the HVAC unit always runs in the lowest stage first before kicking up to the higher output stage. While it looks challenging, it is really fairly easy to install a thermostat with seven wires.
Things You'll Need
- Volt meter
- Drywall anchors and screws
- Cordless drill
- Wire stripper
Turn off the power to the HVAC unit by turning off the correct circuit breaker in the circuit breaker panel. Verify that the power is off by checking the power at the unit with a volt meter.
Take off the HVAC unit access panel and look to see how your thermostat wires are connected to your HVAC unit. For a seven-wire system, a typical configuration would be: the red wire will be on the "R" terminal, the white wire will be on the "W" terminal, the green wire will be on the "G" terminal, the yellow wire will be on the "Y" terminal, the black wire will be on the "C" terminal, the light blue wire will be on the "Y2" terminal and the brown wire will be on the "W2" terminal. Put the access panel back on.
Install the thermostat wall plate to the wall with drywall anchors and screws. Use your level to check that it's level before proceeding.
Connect the thermostat wires to the thermostat in the same fashion that they are connected to the HVAC unit. Strip them, if necessary, so 1/4 inch of bare wire is exposed on the end of the wires.
Install the thermostat to the wall plate. It should snap into place by gently pressing it on. Make sure the thermostat wire doesn't get pinched behind the thermostat when pushing it onto the wall plate. There should be a little depression where the wire is meant to sit.
Turn the power back on to the HVAC unit. Set the temperature to your desired setting, and the HVAC unit will maintain that temperature.
Tips & Warnings
- Keep the thermostat out of a location that is excessively drafty, sunny or can receive heat from an appliance. If mounted in one of these locations, it will not effectively heat or cool your home.
- High Performance HVAC: Thermostat Wire Colors
- Timothy Gonyo; Sheet Metal Workers Local #18; Milwaukee, Wisconsin
- Photo Credit Jupiterimages/Creatas/Getty Images
How to Install a Digital Programmable Thermostat
With utility bills constantly on the rise, it is often up to homeowners to take matters into their own hands to help...
How to Install a Two Wire Thermostat
Depending on the heating system you have, you can have from two all the way up to eight wires that run from...
How to Install a Six Wire Thermostat
The number of thermostat wires varies depending on if you have a furnace, heat pump, air conditioner and how many stages each...
How to Install Thermostat Wires
Home heating systems use thermostats to maintain the correct temperature. Thermostats communicate with the furnace using low-voltage thermostat wires. Each thermostat function...
How to Wire a Thermostat With Blue Wire
Your thermostat is connected to your furnace via a low voltage control wire. This control wire actually has many smaller wires within....
How to Wire a Hunter Thermostat
Wiring a Hunter thermostat requires accuracy; otherwise, you could damage components of the thermostat and your HVAC unit. Some thermostat wiring follows...
How to Replace an 8 Wire Thermostat
If you've ever pulled off your thermostat, you'll notice that there are a number of wires attached to it. These wires run...
How to Wire a Ruud Thermostat
Wiring most thermostats is done in the same manner with minor exceptions depending on the brand and what the specific unit was...
How to Install a New Thermostat
From connecting the wiring to mounting the thermostat to the wall, learn how to install a new or replacement thermostat in this...