Ductile iron pipe (DICL) pipe is used in water and waste water networks. Hydrostatic tests build up the pressure inside of pipes and check for leaks. The minimum pressure standards of DICL pipe depend upon the application.
Minimum Pressure in Hydrostatic Test
Residential water main pipes must hold a pressure of 150 pounds per square inch. In fire protection systems like piping, the test pressure must be at least 200 psi. For fire protection piping kept above 200 psi, the test pressure must be 50 psi over the maintained pressure. The American Water Works Association requires pressure be maintained within 5 psi (34.5 kPa) of the test pressure during hydrostatic testing. Makeup water can be added to the pipe for tiny amounts of water loss as vapor.
The testing allowance or allowed make up water is found by multiplying the length of pipe in feet by the nominal diameter of the pipe in inches. This value is divided by 148,000. The result is multiplied by the square root of the average hydrostatic test pressure. For a 10 foot pipe length with a 10 inch nominal diameter tested at 150 psi, the allowable loss of water in the pressure test is 10 x 10 or 100, which is then divided by 148,000, resulting in 0.0006757. The square root of the test pressure 150 psi is 12.247. The result of 0.0006757 is multiplied by 12.247 gives the 0.0008275 inch-pounds of allowable pressure loss.
Allowable pressure loss is based on American Water Works Association (AWWA) standard C600-82. AWWA standard C600 is shared with the American National Standards Institute (ANSI). American Society for Testing and Materials (ASTM) international standards require hydrostatic testing of DICL pipe be performed before water or sewer pipe is installed.
- Photo Credit Jupiterimages/Photos.com/Getty Images Hemera Technologies/AbleStock.com/Getty Images
Pipe Hydrotest Safety Procedures
Hydrostatic testing uses a high pressure of air or water pumped into a newly installed or repaired pipeline to test the integrity...
- How to Pressurize Natural Gas Pipelines for Leak Detection
How to Train for Hydrostatic Testing on Pipes
Hydrostatic testing is performed on fluid pressure vessels such as holding pipes, pipelines, cylinders and tubes. These tests are critical to evaluate...
How do I Install Mechanical Joint Fittings?
Invented approximately 550 years ago, mechanical joint pipe fittings have become the most prominently used fitting for utility pipe layers and plumbers...
What Are the Piping Sizes of Refrigerant?
Refrigerant piping sizes are determined by the mechanical requirements of the system, including: pressure drop, coolant volume and building layout. Pressure drop...
Classes of Ductile Iron Pipe
Ductile iron pipe is measured by the nominal thickness of the wall of the pipe. In order to know which size to...
Water Pressure Requirements for Private Homes
The water pressure required for a private home, according to the International Plumbing Code, is based on the pressure required by the...