Installing gas piping can be very dangerous. As a result, the Indiana Fuel Gas Code contains information on gas piping, including its installation.
Gas piping should never be installed through a ducted air supply, return or exhaust. These areas include chimneys, laundry chutes, gas vents, dumbwaiters, elevators shafts or ventilating ducts. If installed underneath floors, gas piping should be laid in channels in the floors such that they may be serviced with minimal damage done to the building.
Piping should never be installed underground unless the piping is encased in a conduit made of wrought iron, plastic or steel capable of resisting the additional force.
Often, conduits carry gas from outdoors to the inside of a building. The point at which the conduit meets the gas piping proper inside the building, it is important to ensure that the conduit and the piping are properly sealed to prevent the possibility of leakage.
Why Is a Stand Required for a Gas Hot Water Heater?
A gas hot water heater is required by code to have a stand elevating it above the ground to prevent flammable vapors...
How to Hook Up a Gas Stove
A gas stove uses natural gas in order to cook. This type of stove will have four areas on top that once...
How do I Install a Twin Walled Flue Pipe?
The double-walled structure of a type B gas vent, also called twin-walled flue pipe, provides an additional measure of safety when venting...
Natural Gas Plumbing Pipe Types
Black metal pipe is no longer the only distribution material for natural gas. Many municipalities allow builders to install alternative gas plumbing...